Intermediate (field) (direct and General Support) and Depot Maintenance Manual: Generator Set, Diesel Engine Driven, Tactical : Skid Mtd., 60 Kw, 3 Phase, 4 Wire, 120/208 and 240/416 Volts : DOD Models ... Including Optional Kits .... (Google eBook)
Departments of the Air Force, Army, and Navy (including U.S. Marine Corps), 1990 - Diesel motor
What people are saying - Write a review
We haven't found any reviews in the usual places.
actuator amperes assy bore bracket camshaft CAPACITOR capscrews Check circuit clean clearance coil components connecting rod CONNECTOR coolant crankshaft cylinder block cylinder head cylinder sleeve damaged defective diameter DIODE Disassembly Disconnect engine Exciter FDCED figure flywheel frequency meter fuel injection pump Gasket Governor Control Unit hydraulic head inch indicator Insert Inspect Install insulation JACK CONNECTOR main bearing malfunction Maximum meter nozzle ohmmeter ohms oil pan oil pressure oil pump Operator and Organizational Organizational Maintenance Manual output percent piston pin plate plug position power supply rated load rated voltage Reassembly receptacle RED MKG Refer to Operator relay assembly relay box relay test Remove Repair Replace resistance RESISTOR ring rocker arm rotor seal shaft slots SOLDER solenoid special relay speed spring starter stator switch Table temperature throttle thru Tighten torque transfer pump turbocharger voltage regulator volts Washer Wiring Harness
Page 16-10 - ... voltage and frequency must be made to maintain corrected rated load at rated voltage and frequency. Adjustments to the voltage and frequency shall be limited to those adjustments available to the operator, specifically adjustments to the voltage or frequency adjust devices. On sets with a droop type speed control system as the prime speed control, the speed and droop portions of the control may be adjusted. Adjustments to load, voltage, or frequency controls shall be recorded on the recording...
Page 16-10 - J 1 349 contain instructions for instrumentation and calculations for the ambient condition correction factor (Ref. paragraph 6.2). The engine manufacturer will specify which of the documents should be referred to for each specific engine. 6. Governor Performance Test 6.1 Stabilization — Start and operate the generator set and allow the set to stabilize at rated load, rated voltage, and rated frequency. During this period, operate the recording frequency meter at a chart speed of not less than...