c. Repaired areas and those surfaces requiring refinishing shall be cleaned with a suitable abrasive paper, then primed and repainted.
d. Re-stencil as required.
6-35. REBUILD. Rebuild the control cubicle wire harness (15, figure 6-7) according to figure 6-8.
6-36. REASSEMBLY. Refer to figure 6-7 and reassemble control cubicle assembly in the reverse order of index numbers assigned. Pay particular attention to the following:
a. Install control box relay on rear wall of box (36). Secure in position with four nuts.
b. Refer to Operator and Organizational Maintenance Manual and install components
on control box door (25), and thermal watt converter and frequency transducer in box (36).
c. Install harness (15) connector in box (36) with key way on top. Connect wires of harness to components, refer to figure 1-5.
d. When installing clamp (2, figure 6-7) nearest control box door (25), leave nut (1) loose enough to permit harness to pivot when control box door is opened and closed.
6-37. TEST. Refer to figure 1-5 and perform continuity test of circuitry.
6-38. INSTALLATION. Refer to paragraph 2-6 and figure 2-2 and install the control cubicle assembly.
6-39. ADJUSTMENT. Refer to Operator and Organizational Maintenance Manual and zero adjust all instruments.