What people are saying - Write a review
We haven't found any reviews in the usual places.
Rigid Metal Conduit Air Circuit Breakers
Surface Metal Raceway Induction Motors 11
Calculation of Conductor Sizes SECTION L
1 other sections not shown
amperes apparatus appliances approved for Class armored cable Asbestos bonding jumpers box or fitting branch circuit building busway cabinets Cambric capacitors Circuit Breaker circuit conductors circuit-breakers Class I locations Class III comply Condulets conform to section connected current-carrying capacity cutout boxes disconnecting means Division 2 locations ductors dust dust-tight electrical metallic tubing electrode enclosed enclosures explosion-proof exposed feet fixture wire flexible cord furnace fuses gases grounding conductor hazardous locations horsepower ignitible inches installed insulation junction boxes Knife Switches lampholders lighting fixtures load mechanical injury metal raceway motor-generator National Electrical Code Open conductors operation outlet box overcurrent device overcurrent protection Panelboard paragraph pipe raceway system rating or setting receptacle resistors rigid conduit Rubber seals secondary service conductors specified suitable supply switchboard switches Table temperature terminal Thermoplastic tion transformer ungrounded vapors vault ventilated voltage volts or less wet locations wiring method wiring system