What people are saying - Write a review
We haven't found any reviews in the usual places.
Other editions - View all
adjustable aluminum amount amperes angle armature arranged attached automatic belt boiler bolt bottom carried cast-iron cent chamber circuit coal coils compressed condenser connected consists construction copper crank cutters cylinder diameter discharge disk drill driving dynamo electric electromotive force engine feed field-magnets frame front furnace gear grooves heat holes horizontal horse-power hour iron lathe length lever lower machine magnetic magnetic circuit mechanism metal mill motion motor moved naphtha operation passes pipe piston placed plane plate position pressure projectiles pulley pump resistance reverberatory furnace revolutions revolutions per minute revolving ring rollers rolls rotating screw shaft shown in Fig side sliding speed spindle spring spur-gear steam steel stroke surface temperature tion tons trunnions tube tuyeres upper valve vertical volts water-tube boiler weight wheel wire
Page 67 - The analysis of the flue gases is an especially valuable method of determining the relative value of different methods of firing, or of different kinds of furnaces. In making these analyses great care should be taken to procure average samples — since the composition is apt to vary at different points of the flue.
Page 65 - In preparing for and conducting trials of steamboilers, the specific object of the proposed trial should be clearly defined and steadily kept in view. II. Measure and record the dimensions, position, etc., of grate and heating surfaces, flues and chimneys, proportion of air space in the grate surface, kind of draught, natural or forced.
Page 67 - ... recorded, including the height of the water in the boiler, and the average pressure of steam and temperature of feed during the time. By thus recording the amount of water evaporated by successive portions of coal, the record of the test may be divided into several divisions, if desired, at the end of the test, to discover the degree of uniformity of combustion, evaporation, and economy at different stages of the test. XIV. Priming Tests. In all tests in which...
Page 67 - In tests for purposes of scientific research, in which the determination of all the variables entering into the test is desired, certain observations should be made which are in general unnecessary for ordinary tests.
Page 66 - ... portion. It is desirable that at the same time the amount of water fed into the boiler should be accurately noted and recorded, including the height of the water in the boiler, and the average pressure of steam and temperature of feed during the time.
Page 66 - ... while the water is in a quiescent state, just before lighting the fire. At the end of the test, remove the whole fire...
Page 67 - ... for purposes of scientific research, in which the determination of all the variables entering into the test is desired certain observations should be made which are in general unnecessary for ordinary tests. These are the measurement of the air supply, the determination of its contained moisture, the determination of the amount of heat lost by radiation, of the amount of infiltration of air through the setting, and (by condensation of all the steam made by the boiler) of the total heat imparted...
Page 65 - Water meters, as a rule, should only be used as a check on other measurements. For accurate work, the water should be weighed or measured in a tank. 3. Thermometers and pyrometers for taking temperatures of air, steam, feed-water, waste gases, etc.
Page 65 - Have an understanding with the parties in whose interest the test is to be made as to the character of the coal to be used. The coal must be dry, or, if wet, a sample must be dried carefully and a determination of the amount of moisture in the coal made, and the calculation of the results of the test corrected accordingly.