What people are saying - Write a review
We haven't found any reviews in the usual places.
PerformanceBased Option 1
19 other sections not shown
accor accordance with NFPA accordance with Section aircraft aisle apply approved assembly automatic sprinkler system bales building ceiling CFRS Chapter Class classification Code combustible liquids compressed gases construction consumer fireworks containers cryogenic cylinders detectors devices Dibenzoyl peroxide discharge doors edition electrical emergency equipment exceed exit explosive facilities fire alarm system fire barrier fire extinguishers Fire Tests flash point floor hazardous materials heat hose ignition inspection installed in accordance intermediate bulk containers less limited Liquefied Petroleum Gas located LP-Gas maintenance maximum means of egress ment minimum NFPA 13 NFPA 30 NFPA 58 noncombustible occupancies operations organic peroxide oxidizers permitted pile piping pressure pump Pyrophoric quantity racks safety smoke smoke detectors space specified spray area Standard storage area stored structure system in accordance Table tank temperature tion valve vapors vehicle vent ventilation wall